Note: All orders with merchandise totalling less than $50.00 are charged a Minimum Order Fee of $10.00 It will automatically added to your S&H. Buy more, save more!
Complete Unit 120V 500-1000-1500W (RMC151W)
Cadet 63315 Complete Unit 120V 500-1000-1500W (RMC151W)
Features and Benefits
- High temperature manual reset: turns off heater if normal operating temperatures are exceeded
Commercial grade steel element
Powder coat paint process eliminates sharp metal edges
Wall can designed for quick installation with mounting legs that minimize measuring time
The Register Plus is Cadet's premier fan forced heater line and is often chosen for its similar appearance to central system register vents. Models are offered with both fixed and multi-watt capabilities (multi-watt models factory preset at their maximum wattage). A large squirrel cage blower quietly provides increased airflow allowing for lower surface and air-at-surface temperatures. Cadet recommends a wall-mounted thermostat for optimum performance, or you may prefer the convenience of an
optional field mount thermostat kit
Fan forced electric air heaters shall be UL Listed, factory rated at 120V, 208V, or dual field rated 208V/240V. A 20 gauge wall mounting can with four knockouts shall be provided with each complete heater. The element and blower shall be of unitized construction and shall attach to wall can with a single screw. Elements shall be steel-finned type, with an oversized 25 amp rating at 240V high temperature manual reset limit switch. A tangential cylindrical blower delivering approximately 60 CFM (RM202), and 50 CFM (RM162 and RM151) shall be driven by an impedance protected motor with permanently lubricated, vibration isolated, dust sealed bearings. Metal grill shall be of one piece construction and finished with a powder coat paint system.
A thermostat is required. For optimum comfort use a Cadet electronic thermostat. Fan heaters and thermostats work best when installed on an inside wall. A double pole, built-in thermostat may be installed in the field. UL requires heater to be placed a minimum distance of 6 (15.2 cm) from adjacent surfaces and 4.5 (11.4 cm) from the floor. Manufacturer recommends installation of 12 from all surfaces. A 3 (91.44cm) minimum clearance is recommended for furniture or other objects placed directly in front of heater.
NOTE: Manufacturer recommends installing heater assembly after walls are finished. Heater must be cleaned every six months minimum.
Recommended for elevations under 7500 feet. Complete unit available in white only.
Rough In Dimensions: 12.75"W x 6"H x 4"D
Wall Can Dimensions: 12.625"W x 8.875"H x 4"D
Grill Dimensions: 14"W x 7.375"H
Part Number: 63315
UPC Code: 027418633156
Model Number: RMC151W
Description: Complete Unit
Watts 120V: 500/ 1000/ 1500
Amps 120V: 4.17/ 8.33/ 12.50
Carton Dimensions: 14.375W x 9.375H x 5.75D
________________________________________________________________________________________________ Need more information? Call us at 1-800-89-READY.
Looking for the best deal for a volume order? Request for Quotation
For HI, GU, AK, PR and "Will-Call" or "In-Store Pickup" customers, please read the Terms & Condition (Shipping Information)
, before placing order.
Find an error on this page? Please let us know, Contact Us.